Wiring FACP + Next IDC Pull Station 51378 To meet UL requirements for outdoor use, the BG-12LO pull station must be to the SB-I/O backbox to create the BG-12LOB model. The BG-12LO, with the backbox, is UL approved in retrofit applications. Gasket not cover any connections) Do not loop wiring under any Break wire run to IDC supervision. Manual Pull Station for Outdoor Applications) U.S. Patent No. Des. 428,351; 6,380,846; Other Patents Pending 51378 BG-12LO and BG-12LOB pull stations are non-coded, dual-action manual pull stations a key-lock reset feature, an approved outdoor gasket, and an accompanying outdoor (BG-12LOB only). They provide Fire control panels with one normally open alarm initiating input. The BG-12LO/-12LOB meet the ADAAG controls and operating guidelines (section 4.1.3), and the ADA requirement for a 5 lb. maximum force to activate the pull station. Operating instructions are molded into the pull station along with Braille text. Molded terminal numbers are also present. gold plated switch contact (N/O) is sealed for reliability and rated at 0.25 A at 30 volts or DC). supplied Outdoor Backbox (SB-I/O) is surface mounted using the incorporated mount- bosses. The backbox can be positioned to allow conduit from any side and the pull will mount in any position. Use the (4) screws provided to mount the pull station the backbox. activate the dual-action pull station, push in and pull down on the handle. The word appears after the handle is pulled down. This will remain until the pull sta- is reset. pull station includes one Single Pole, Single Throw (SPST) Normally Open (N/O) which closes upon activation of the pull station. the Pull Station Insert the key into the lock and rotate 1/4 turn counterclockwise. Open the door until the handle returns to normal. Close and lock the door. Closing the door automatically resets the switch to the position. Open- the door will not activate or deactivate the alarm switch. Do not detach the door of the pull station during installation. The door of pull station cannot be reattached to the backplate after the backplate has already been onto an electrical box. the Fire BG-12LO/-12LOB pull stations in accordance with these instructions, NFPA standards, national and local Fire and Electrical codes and the requirements the AHJ (Authority Having Jurisdiction). Regular testing of the devices should be con- in accordance with the appropriate NFPA standards. Failure to follow these directions result in failure of the device to report an alarm condition. Fire is not responsible for that have been improperly installed, tested or maintained. Compliance ADA compliance, if the clear floor space only allows forward approach to an object, the forward reach height allowed is 48 inches (121.92 cm). If the clear floor space parallel approach by a person in a wheelchair, the maximum side reach allowed is inches (137.16 cm).