InstallatIon anD maIntenance InstructIons FireLite Place CT 06472 203.484.7161 Dual monitor module to 32 VDC mA (LED on) (LED flashing) Ohms Ohms Ohms Volts to 120 (0 to 49 to 93% Non-condensing in H 4.275 in W 1.4 in D (Mounts to a 4 in square by 21/8 in deep box.) Electrical Box Operating Voltage: Current Draw: Operating Current: Resistance: SLC Wiring Resistance: IDC wiring resistance: IDC Voltage: IDC Current: Range: InstallIng information is included as a quick reference installation guide. Refer to control panel installation manual for detailed system information. If the will be installed in an existing operational system, inform the opera- and local authority that the system will be temporarily out of service. Dis- power to the control panel before installing the modules. directly to 4-inch square electrical boxes, Figure 2A). The box must a minimum depth of 21/8 inches. Surface mounted electrical boxes are available from FireLite. 2. moDule mountIng: This manual should be left with the owner/user of this equipment. DescrIptIon Dual Monitor Module is intended for use in addressable, two wire sys- It provides two independent 2-wire initiating device circuits (IDC), at separate, consecutive addresses. It is capable of monitoring normally contact fire alarm and supervisory devices, or either normally open or closed security devices. requIrements ensure proper operation, this module shall be connected to a compatible system control panel (list available from FireLite). 1. removIng rotary swItch stop: All wiring must conform to applicable local codes, ordinances, and This module is intended for power limited wiring only. Install module wiring in accordance with the job drawings and appropri- wiring diagrams. Set the address on the module per job drawings. NOTE: Monitor module L (using terminals 6 and 7) responds at the ad- set on the code switches. Monitor module H (using terminals 8 and will automatically respond at the next higher address. For example, if code switches are set to 76, module L will respond at address 76 and H will respond at address 77. Use caution to avoid duplicate ad- of modules on the system. Secure module to electrical box (supplied by installer), as shown in 2. 3. typical 2-wire initiating circuit configuration, nfpa style B: NEXT PANEL OR DEVICE INITIATING DEVICE CIRCUITS (L&H), EACH LIMITED TO 240 @ 11 VDC MAX. 47k EOL 47k EOL MODULES TO LISTED CONTROL PANELS ONLY LINE CIRCUIT (SLC) VDC MAX. SHIELDED-TWISTED IS RECOMMENDED LISTED CONTACT CLOSURE DEVICES MAY USED. DO NOT MIX FIRE ALARM INITIATING, OR SECURITY DEVICES ON THE INITIATING DEVICE CIRCUIT. CONTACT CLOSURE DEVICES PER INSTALLATION INSTRUCTIONS. WIRING SHOWN IS AND POWER LIMITED L (TERMINALS 6 & 7) RESPONDS AT ADDRESS ON CODE SWITCHES. MONITOR H (TERMINALS 8 & RESPONDS AT NEXT HIGHER ADDRESS. FireLite Alarms, Inc.