TECH/DATA SHEET Controller Enclosure 1 1 1 2 2 2 3 3 3 4 4 4 5 5 5 6 6 6 7 7 7 8 8 8 H G Card Enclosure sLON-7 Controllers are programmable, LONWORKS based control devices. sLON-7 Series Controller features eight universal four analog outputs, eight digital outputs, a volt reference, LED indication, and support for sensors. Additionally, network capability provided through the use of a FTT-10 transceiver the controller to communicate to other devices part of a LONWORKS Free Topology network. A direct connection to a Communication adapter and a PC with Software Tool is necessary to download and applications applications include central station air VAV air handlers, fan coil units, unit and cooling towers. Chart Wall-Mount Enclosure Enclosure Card with Backed-up Time items not provided) carton for damage. If notify carrier Inspect for damage. damaged products must be a experienced Job wiring diagrams Tools: Drill and bits for Corporation – www.solidyne.com rev1 03/2005 mounting screws Digital Volt-ohm meter (DVM) Static protection wrist strap Class 1 or Class 2 power transformer supplying a nominal 24 Vac (20.4 to 30 Vac) with minimum rating of 20 VA, 50/60 Hz per controller plus Digital Output (DO) loads (if transformer is used). In European Community, transformer must conform to standards. Terminators: One sLON-T1 terminator required for free topologies Two sLON-T2 terminators required for bus topologies Electrical shock hazard! Disconnect power before installing or removing the Follow Static precautions when installing this equipment. Use copper conductors that are suitable for 167 (75 Make all connections according to electrical wiring diagram, national and local electrical Precautions charges damage electronic components. The microprocessor and associated circuitry extremely sensitive to static discharge. Use the following precautions when installing, or operating the system. Work in a static-free area. Discharge static electricity by touching a known, securely grounded object. Use a wrist strap connected to earth ground when handling the controller printed board. Communications Commission (FCC) equipment has been tested and found to comply with the limits for a Class B digital pursuant to Part 15 of the FCC Rules. These limits are designed to provide protection against harmful interference in residential installations. This generates, uses, and can radiate radio frequency energy and may cause harmful if not installed and used in accordance with the instructions. Even when are followed, there is no guarantee that interference will not occur in a particular If this equipment causes harmful interference to radio or television reception can be determined by turning the equipment off and on user is encouraged to to correct the interference by one or more of the following measures: Reorient or relocate the receiving antenna. Connect the equipment to an outlet on a circuit different from that to which the receiver the separation between the equipment and receiver. connected. Consult the dealer or an experienced radio/television technician for help. Department of Communications (DOC) class B digital apparatus meets all requirements of the Canadian Interference-Causing Regulations. appareil numerique de la classe [B] respecte toutes les exigences du Reglement sur le broilleur du Canada. Community Directives equipment meets all requirements of European Community Directives for Low Voltage and Electromagnetic Compatibility (89/336/EEC).